1 INSTALLATION PRECAUTIONS …………21-1 BEFORE INSTALLATION …………….21-2 PARTS IDENTIFICATION …………….31-3 KNOCKOUTS …………………………….32 DETECTION AREA……………………………42-1 OUTLINE OF DETECTION AREA …42-2 HOW TO REDUCE THE LONG RANGE DETECTION AREA …………62-3 HOW TO DEACTIVATE THE SHORT RANGE DETECTION AREA …………83 INSTALLATION ……………………………….10
HX-80N2 PIRs standard modelHX-80NAMHX-80N with anti-maskingIntelligent AND logicVegetation sway analysis logicINSTALLATION INSTRUCTIONS
Warninghandling may cause death or serious injury.
Failure to follow the instructions provided with this indication and improper The check
mark indicates recommendation.The nix
sign indicates prohibition.
Keep product away from waterMount the unit securelyMounting height
Sunlight and reflection?Heat source?Objects moving in the wind ?
(8’2″ ? 9’10”)
For jointFor wall mounting
OUTLINE OF DETECTION AREA
DETECTION AREA (factory default)
jgdjgd4812162024(m)4812162024(m)102030405060708010203040506070801020304050607080Top ViewSide View4812162024(m)
HOW TO REDUCE THE LONG RANGE DETECTION AREATo adjust the LONG range of detection, set the upper and lower flaps as follows:
Pull out the flap.
If the lower flap is located at the factory default position, slide it out with your thumb.
Move the flap to the position that
Push the flap until it clicks into position.
1. The distance may vary due to environmental conditions.2. Always walk test the detector to confirm the detection distance.
(80′)aN.A.(42’8″)18.0 m(60′)(32’10”)6.5 m(22′)
default LowerUpperFactory default
Upper position: a, Lower position: Factory defaultUpper position: a, Lower position: bUpper position: c, Lower position: bUpper position: c, Lower position: d
HOW TO DEACTIVATE THE SHORT RANGE DETECTION AREATo adjust the SHORT range of detection, set the upper and lower plates as follows:
Remove the plate.
Insert the plate into the position determined by the required masking
If any plate is not used, place it in the
Be careful not to lose the plates.
Use the following table to determine the positions of the plates that set the required masked area.NOTE: Use only the following combinations for the plate settings.
UpperNot usedNot used
Upper position: Factory default, Lower position: jUpper position: i, Lower position: jUpper position: i, Lower position: hUpper position: g, Lower position: h
Use the bracket for normal installation. The unit may be installed directly on the wall, without Horizontal adjustment is not necessary.
INSTALLING WITH BRACKET
Remove the Up-Down lock screw.
Push the shaft cover clip straightly to remove the shaft cover.
e.g. small screwdriverShaft coverShaft cover clip
Loosen the adjustment screw two turns.
Adjustment screwscrew too much.
Tilt the bracket about 45? and pass
Determine the horizontal direction (left or right) of the detector before installing the
Open the wiring knockout.
Open the Up-Down lock screw knockout
To the right
To the leftAdjustment
Tighten the adjustment screw clockwise.
Wire to the terminal and install the main unit and lens on the base.
– 11 –
ADJUSTING THE VERTICAL ANGLEDecide the detection length. To change the detection length, adjust the flap and plate
Example (the ground is level)
INSTALLING WITHOUT BRACKET
Open the wiring knockout with suitable tool e.g. screwdriver.
Pull the wire through the base knockout.
Adjustment If the detection length is shorter than that which was setup (refer to page 7), change If the detection length is longer than that which was setup (refer to page 7), change the If the detection length is equal to that which was setup (refer to page 7), the Adjust 1 click (1.25? upward) for 3.0 m (9’10”) height installation.
Fasten the base to the wall.
Install main unit after wiring to the
Power wires should not exceed the following lengths.
HX-80NHX-80NAM12 V14 V12 V14 VAWG22 (0.33 mmAWG20 (0.52 mmAWG18 (0.83 mm
TAMPER terminals to be connected to a 24 hour supervisory loop.TAMPER OUTPUTSPARE (Non short)ALARM OUTPUT (N.O.)ALARM OUTPUT (COM)ALARM OUTPUT (N.C.)POWER INPUT (-) (9.5 – 18VDC)POWER INPUT (+) (9.5 – 18VDC)
WALL TAMPER (OPTION)Universal magnet switch may be mounted as a wall tamper.
Magnet switch (Wall side)Magnet switch (Wall side)
Install the magnet switch (wall side) to the wall. To determine the installation position, use the ?Installation position template? provided on the inside cover of the product
tool e.g. screwdriver.
Install bracket and the main unit to the walls surface.
Tilt the bracket about 45? and
Set the DIP switch 1 (LED ON/OFF) to
The switch is set ?ON? by factory
Check that the detector detects an
(3’3″) away from the detector.
all times, set the DIP switch 1 (LED
DIP switch1. LED ON/OFF3. AUX INPUT4. PIR AND/OR
POSITIONFUNCTIONIMMUNITY logic is not activated.IMMUNITY logic is activated. Use this under
and correct false alarms. The secondary unit must have a voltage free N.C. output such as another PIR detector or AIR detector.
POSITIONFUNCTIONWalk test to readjust the detection selected. Actual adjustment should be alarm continuously.
POSITIONFUNCTIONHIGHHigh sensitivityLOWLow sensitivity
POSITIONFUNCTIONHIGHHigh sensitivityOFFDisabledAfter closing the cover, do not leave any objects closer than 1 meter from the unit.
DETECTOR CONDITIONLED INDICATOR (RED ONLY)Warm-up
Blinks 2 times and goes off for 5 sec. and then
Blinks 3 times and goes off for 3 sec. and then
ModelHX-80NHX-80NAMDetection methodPassive infraredPIR Coverage24.0 m ? 2.0 m (80′ ? 6’7″) narrow / 20 zones PIR distance limit6.5 m, 10.0 m, 13.0 m, 18.0 m (22′, 33′, 42′, 59′)Detectable speed0.3 m/s ? 1.5 m/s (1’/s ? 4’11″/s)Sensitivity2.0?C (3.6?F) at 0.6 m/sPower input9.5 ? 18 V DC35 mA (max.) 40 mA (max.) Alarm period2.0 ?1 sec.Warm-up periodApprox. 60 sec. (LED blinks)Alarm outputForm C 28 V DC 0.2 A (max.)Tamper outputN.C. 28 V DC, 0.1 A (max.) N.C. open when cover removed.Trouble output?N.C. 28 V DC, 0.1 A (max.)Aux inputN.C. 28 V DC, 0.1 A (max.)LED indicatorRed: Warm-up, AlarmRed: Warm-up, Alarm, TroubleRF interferenceNo alarm 10 V/mWeatherproofIP55 MountingWallMounting height2.5 ? 3.0 m (8’2″ ? 9’10”) Vertical: ?20? Horizontal: ?95?Weight720 g (25.4 oz.)AccessoriesBracket, Screw (4 ? 20 mm) ? 4
93 (3.66)197.5 (7.78)
responsibility for any damages or other consequences resulting from an intrusion. Using bracketUnit: mm (inch)Without bracketUnit: mm (inch)
TEL:+1-909-993-5770Tech:(800)966-7839 URL:http://www.optex.com.pl/TEL:+86-755-33302950URL:http://www.optexchina.com/OPTEX CO., LTD. (JAPAN)(ISO 9001 Certified) (ISO 14001 Certified)OPTEX (EUROPE) LTD. (UK)TEL:+44-1628-631000URL:http://www.optex-europe.com/URL:http://www.optex-security.com/
Para poder atenderte mejor necesitamos conocer: